raw water（wells, lakes, rivers, and tap or other water souce→ 1 booster pump→ 2 sand(multi-medium) filter(or Manganese for iron removal)→3 active carbon filter→4 water softener (optional)→
5 security(micron/PP) filter→6 high pressure pump→7 reverse osmosis system→ 8 UV sterilizer (ozone generator) →pure water storage tank
Function of each part of water treatment plant
1.booster pump-- provide the pressure to quartz sand filter/active carbon filter
2.Multi-medium filter-- get rid of turbidity, suspended matter, organic matter, colloid, ect.
3.Active Carbon filter--Remove the color, free chloride, organic matter, harmful matter, ect.
4.Softener--exchange "ions" of calcium and magnesium with the most common and easiest method.
5.Security filter--prevent large particles, bacteria, viruses into RO membrane, accuracy is 5um
6.High pressure pump-- Provide the high pressure to RO membrane
7.RO system-- main part of the plant. 4040membrane ,4"*40" high flow RO membrane,LCLE-4040 Brackish water RO membrane ,The RO membrane's desalting rate can reach 99%, removing over 99% ions
8.UV sterilizer or ozone generator--- kill bacteria
The process of reverse osmosis deals with the use of a high pressure pump which applies extreme pressure to the high saline concentrated side of membrane, combatting a natural process
called "Osmosis". Naturally, osmosis transports salt through a semi-porous membrane from a region with low saline concentration to a region with high saline concentration. Its goal is to gain an
equal quantity of saline concentration on both sides of the membrane. With the use of the high pressure pump, reverse osmosis comes in to direct osmosis to the opposite direction. The pump
applies high pressure to the highly concentrated saline side of the membrane, pushing salty water and other impurities across the membrane, only allowing water molecules to flow through. Salt and
the impurities are rejected and later thrown into the drain on the concentrate side. In the end, user obtain purified water with 99% less dissolved salts on the permeate side of the
Commercial RO ,Reverse Osmosis system ,pre and past treatments, 1500GPD/250LPH, 3000GPD/500LPH,4500GPD/750LPH,6000GPD/1000LPH,12000GPD/2000LPH.
Standard commerical RO system available for clients
one to one solution design for each clients are available. just send your raw water quality and required water quality ,your detailed and specifcated requests of water capacity and target water
quality will very helpful for the system design.